## ARC FLASH BOUNDARIES AND SAFE DISTANCE BASICS FOR POWER PLANTS

Arc-flash boundaries need to be established around electrical equipment such as switchboards, panel boards, industrial control panels, motor control centers, and similar equipment if you plan to work on or in the proximity of exposed energized components.

Parts are considered exposed if they are energized and not enclosed, shielded, covered, or otherwise protected from contact. Work on these parts includes activities such as examinations, adjustment, servicing, maintenance, or troubleshooting.

Equipment energized below 240 V does not require arc-flash boundary calculation unless it is powered by a 112.5 KVA transformer or larger. The arc-flash boundary is the limit at which a person working on energized parts can be standing at the time of an arc-flash without risking permanent injury unless they are wearing flame-resistant clothing.

Permanent injury results from an arc-flash that causes an incident energy of 1.2 calories/centimeter2 (cal/cm2) or greater and causes a minimum of second-degree burns. This distance can only be effectively determined by calculating the destructive potential of an arc.

First you must determine the magnitude of the arc based on the available short circuit current, then estimate how long the arc will last based on the interrupting time of the fuse or circuit breaker. Finally, you will need to calculate how far away an individual must be to avoid being exposed to an incident energy of 1.2 cal/cm2.

It may sound like a lot of math and factoring in of potentials, but believe me the extra time you take to determine the arc flash boundary is well worth your safety and well-being.

Calculating flash protection boundaries for systems over 600 V requires performing a flash hazard analysis coupled with either the NFPA 70E Hazard Risk Category/PPE tables or the Incident Energy Formula.

Additionally, Section 4 of IEEE 1584 Guide for Arc Flash Hazard Calculations states that the results of the arc flash hazard analysis are used to identify the flash-protection boundary and the incident energy at assigned working distances throughout any position or level in the overall electrical system. The purpose is to establish safe work distances and the PPE required to protect workers from injury. A flash-hazard analysis is comprised of the following three different electrical system studies:

- A short circuit study
- A protective device time-current coordination study
- The flash-hazard analysis and application of the data

Arc flash hazard analysis
To perform an arc flash hazard analysis, you need to start by gathering information on the building’s power distribution system. This data should include the arrangement of components on a one-line drawing with nameplate specifications of every device on the system and the types and sizes of cables.

The local utility company should be contacted so that you can get the minimum and maximum fault currents entering the facility. Next you will want to perform a short circuit analysis and a coordination study. You will need this information to put into the equations provided in NFPA 70E or the IEEE Standard 1584.

These equations will give you the flash protection boundary distances and incident energy potentials you will need to determine your minimum PPE requirements. In many ways an arc fault analysis is actually a study in risk management.

You can be very conservative in your analysis and the results will almost always indicate the need for category 4 PPE. On the other hand, you can perform the analysis and make adjustments to reduce the arc fault conditions resulting in reduced PPE requirements.

However, use caution when adjusting your calculations. Reducing the bolted fault current can reduce the arc fault current, but it can actually result in a worse situation. For example, if you reduce the current applied to a motor from 4000 to 1800 A, the arc fault energy is increased from 0.6 to 78.8 cal/cm2. This is the exact opposite outcome that you might expect to achieve before doing the math.

Keep in mind that you are risking OSHA violations and fines if you choose nominal compliance. On the other hand, you can actually be increasing the risk of injury if you force workers to unnecessarily wear cumbersome PPE.

This can also result in little or no high voltage maintenance being performed, which will eventually compromise safety and proper equipment operation. It might prove beneficial to get a registered professional engineering firm to perform arc flash hazard calculations on your behalf and have them recommend appropriate actions and the lowest appropriate category of PPE.

## Related post

for ict 99 said...
anvianu said...

I have to voice my passion for your kindness giving support to those people that should have guidance on this important matter.
safety course in chennai
nebosh course in chennai

daphnemohara said...

Nice post. Such a wonderful information. Thanks for sharing your post. Easy to read and understand. Keep posting.
Fire and Safety Course in Chennai
Safety Institute in Chennai
IOSH Course in Chennai
NEBOSH Safety Course in Chennai
ISO Consultants in Chennai
Electrical Safety Audit

Aparna said...

Oracle Training in Chennai
Oracle Training institute in chennai
Excel Training in Chennai
Job Openings in Chennai
Placement in Chennai
Pega Training in Chennai
Oracle DBA Training in Chennai
Tableau Training in Chennai
Power BI Training in Chennai
Social Media Marketing Courses in Chennai

Reshma said...

Selenium Training in Chennai
Selenium Training in Bangalore
Selenium Training in Coimbatore
Selenium Training Institute in Chennai
Best Selenium Training in Bangalore
Best Selenium Training in Coimbatore
Ethical Hacking Course in Bangalore
Tally Course in Chennai

menon said...
dhishageetha said...
Photo Tour said...

There are a handful of fascinating points in time here but I do not know if every one of them center to heart. There may be some validity but I am going to take hold opinion until I take a look at it further. Great article , thanks so we want far more! Added to FeedBurner too https://royalcbd.com/faq/

greatmetal said...

I agree with a lot of the points you made in this article. If you are looking for the Duplex Flanges, then visit Great Metal. I love your content, they are very nice and very useful to us and this text is worth everyone’s attention.

tarangsteel said...

Thanks for such a pleasant post. This post loaded with lots of useful information. Keep it up. If you are looking for the best information and suggestions related to Hastelloy C276 Plate then visit Tarang Steel

fastwellin said...

Hi there to everyone, the contents present at this web page are actually amazing for people knowledge, well, you can also visit 316 Stainless Steel Pipe for more Fastwell related information and knowledge. Keep up the good work.

aesteiron said...

Nice reading, I love your content. This is really a fantastic and informative post. Keep it up and if you are looking for Carbon steel pipe then visit Aesteiron Steels LLP

rajtilakmetal said...

Your blog is awfully appealing. I am contented with your post. I regularly read your blog and its very helpful. If you are looking for the best alloy steel flanges, then visit Rajtilak Metal. Thanks! I enjoyed this blog post.

I found so many interesting stuff in your blog especially its discussion. Get the management Consultant in Canada by experts at modadevelopments.com.

oshwin said...

This is a great article with lots of informative resources. I appreciate your work this is really helpful for everyone. Check out our website Stainless Steel Heat Exchanger Tubes for more Oshwin Overseas. related info!

nisharoshan said...

Really it as an awesome article...very interesting to read..You have provided an nice article....Thanks for sharing.

Web Designing Training in Chennai

Web Designing Course in Chennai

Web Designing Training in Bangalore

Web Designing Course in Bangalore

Web Designing Training in Coimbatore

Web Designing Training

Web Designing Online Training

mage_synmac said...

Thanks for sharing such an informative.
if you required any TAX and GST Consultants, plse visit
synmac consultants in BANGALORE | CHENNAI | DELHI
SYNMAC.IN | GST CONSULTANTS IN BANGALORE | GST RETURN FILING IN BANGALORE | TAX CONSULTANTS IN BANGALORE | COMPANY REGISTRATION IN BANGALORE | GST REGISTRATION CONSULTANTS IN BANGALORE

Roopam Steel said...

Thanks for share your blog here .
Duplex Steel Sheet

RELIABLE PIPES & TUBES LTD said...

This blog is really helpful to deliver updated educational affairs over internet which is really appraisable. I found one successful example of this truth through this blog. I am going to use such information now.
Stainless Steel Reducer

RELIABLE PIPES & TUBES LTD said...

This blog is really helpful to deliver updated affairs over internet which is really appraisable.Stainless Steel Stub Ends

Navstar Steel Corporation said...

Thanks for share your blog here .

Aluminium Die Casting said...

Aluminium Die Casting

Multi Metals India  said...

It is really a helpful blog to find some different source to add my knowledge.
Carbon Steel Seamless Pipe

Micro Metals said...

Impressive and powerful suggestion by the author of this blog are really helpful to reduce our hack-tic life. My own views are matching with author and I have experienced such.
Stainless Steel 304l Round Bar

Interharex Consulting Engineers said...

Excellent information, I am heartily thankful to you that you have shared this information with us. I got some different kind of knowledge from your article, and it is helpful for everyone. Thanks for share it. Composite structures consultants Sydney

William Jessie said...

Μεγάλη δουλειά για τη δημοσίευση ενός τόσο ωραίου άρθρου Το άρθρο σας δεν είναι μόνο χρήσιμο, αλλά είναι επίσης πολύ ενημερωτικό. Σας ευχαριστούμε γιατί είστε πρόθυμοι να μοιραστείτε πληροφορίες μαζί μας.Διαιτολόγος για απώλεια βάρους Βόρεια Προάστια

nickelalloysonlinepipe said...

After going through your contents I realize that this is the best of my knowledge as it provides the best information and suggestions. This is very helpful and share worthy. If you are looking for the best duplex 2205 round bar then visit Raaj Sagar Steels. Keep sharing more.

William Jessie said...
This comment has been removed by the author.
Laura Bush said...

I admire this article for the well-researched content and excellent wording. I got so involved in this material that I couldn’t stop reading. I am impressed with your work and skill. Thank you so much.Ai Sound Monitoring System In Malaysia

highpressurepipefittings said...

Amazing content, a lot of amazing websites which is actually new for me
stainless steel pipe fittings manufacturers

Oil And Gas Piping Materials said...

I must thank you for the efforts you’ve put in penning this blog. I’m hoping to view the same high-grade content by you later on as well. In truth, your creative writing abilities has inspired me to get my own blog now
Alloy Steel Pipe Suppliers

aesteiron said...

Greetings! Very useful advice in this particular post! It’s the little changes that will make the largest changes. Many thanks for sharing!
stainless steel pipe suppliers

Steel Pipe Fittings said...

I truly appreciate this post. I’ve been looking everywhere for this! Thank goodness I found it on Bing. You’ve made my day! Thank you again
stainless steel pipe fittings manufacturers

Regal Sales Corporation said...

After read this post I understand new things and Knowledge of this. I find latest information about this topic Stainless Steel Flanges manufacturer in India If you wants relevant services then visit Regal Sales Corporation.

ERTUĞRUL DOĞAN said...
İlknur Pekşen said...
Unknown said...
Unknown said...
Unknown said...
Iticookshappiness said...

Good to learn something new. Found something on Newzel that will help

Unknown said...
Unknown said...
Anthony Marc said...

Nice info, I am very thankful to you that you have shared this special information with us. I got some different kind of knowledge from your web page, and it is really helpful for everyone. Thanks for share it. emergency exit light testing requirements.

christianharvey said...

I read the above article and I got some knowledge from your article.test and tag adelaide. It's actually great and useful data for us. Thanks for share it.

Unknown said...
Unknown said...
Innomatics said...

I have to thank you for the time i spent on this especially great reading !! i really liked each part and also bookmarked you for new information on your site.